Saving Diesel Fuel for Diesel Gensetby Dieselgenerator Tech ***
How to achieve the most fuel-efficient effect of 1500KW
diesel generator set is the continuous goal of every diesel generator set user
and manufacturer. Guangxi Dingbo generator set factory tutors how to make
diesel generator set more fuel-efficient.
1. Increase the temperature of cooling water
The increase of cooling water temperature can increase the body
temperature of the generator set, which can not only promote the complete
combustion of diesel oil, but also reduce the viscosity of engine oil, so as to
reduce the resistance of movement and achieve the effect of fuel saving.2. Clean the diesel fuel before using
About 60% of the faults of the diesel generator set come from the
oil supply system, so it must be handled before adding oil to the generator
set. The treatment method is as follows: the purchased diesel oil can be used
after being deposited for about 2-4 days, which can precipitate about 98% of
the impurities. If it is purchased and used now, two layers of silk cloth or
toilet paper can be placed at the refueling filter screen of the oil tank. The
purpose of oil treatment is to make the diesel generator set fuel more fully
3. Run the generator set within the rated
power, do not overload.
When using the generator set, it is best to be within the rated
power and do not overload it, otherwise it will achieve the purpose of fuel
saving. Overload operation not only affects the service life of the generator
set, but also greatly increases the oil consumption. Generally, the load rate
is controlled at a reasonable level, and the load rate is between 50% and 80%,
which is more fuel-efficient.
4. Increase the diesel engine belt pulley.
Properly increasing the diesel engine pulley can increase the
speed of the water pump when the diesel generator set is running at a reduced
speed, so as to increase the flow and head, so as to achieve the purpose of
5. Regularly maintain the diesel generator
When the engine is used for a long time, it will form normal wear.
If it is not maintained properly, it will form abnormal wear, resulting in
longitudinal pull marks on the cylinder liner of the diesel generator, the
cylinder diameter and piston side clearance exceed the specified value, the
supporting force of the piston ring will be reduced accordingly, and there will
be unclean oil scraping.
Secondly, the inner support torsion spring in the oil ring is
disconnected at the opening of the oil ring, resulting in unclean oil scraping
and participation in combustion, resulting in serious oil consumption symptoms,
which are manifested in difficult starting of the diesel engine, obvious blue
smoke from the exhaust pipe and
serious oil injection of the respirator.
In addition, the upward side of the piston makes the combustion
chamber form an inverted state due to the inversion of the direction during
assembly. Although it will not affect the start of the diesel engine, the loss
of engine oil will be quite serious. The oil consumption of engine oil is about
0.5kg per day, so it is necessary to maintain the diesel generator set
6. Ensure that the machine does not leak oil.
The oil delivery pipe of diesel generator often has loopholes due
to uneven joint surface, gasket deformation or damaged surface. The solution is
to coat the gasket with valve paint, grind it on the glass plate and straighten
the oil pipe joint. A diesel recovery device is added, and the return pipe on
the oil nozzle can be connected with the air core screw.
7. Maintain the best oil supply angle.
If the oil supply angle deviates, the oil supply time will be too
late and the fuel consumption will increase greatly.
Mob:+86 134 8102 4441
Tel:+86 771 5805 269
Fax:+86 771 5805 259
Skype:+86 134 8102 4441
Add:No.2, Gaohua Road, Zhengxin Science and Technology Park,
Nanning, Guangxi, China
Created on Jan 10th 2022 21:47. Viewed 536 times.