Basic Working Conditions of Diesel Generator Setby Generator D. Diesel Generator
The working conditions of diesel generator set is that it can output the rated power under the condition of prescriptive environment, and also can work reliably and continuously.
The working conditions of power plants (units) stipulated by the national standard is mainly determined by the altitude, ambient temperature, relative humidity, mold, salt fog and the degree of inclination.
The standard working conditions should be adopted to determine the rated power of the diesel genset.
Due to the diesel engine, AC synchronous generator and the control device have its own rules and standards in the national standard, so in the selection and determination of the genset working conditions, these factors should be considered, and it should be based on diesel engine.
According to GB/T 2819-1995 “General Technical Requirements of Mobile Power Station” stipulation, the environment conditions of the rated power outputed by the power station shall be one of the following requirements and shall be explicitly defined in the product technical conditions.
Relative air humidity
The diesel genset shall be capable of outputting the specified power (allowing correction) and working reliably under the following conditions.
Ambient temperature: Upper limit value: 40°C，45°C，50°C
Lower limit value: -40°C，-25°C，5°C
Degree of inclination: For the diesel power station, the vertical and horizonal gradient of the power station is not beyond 10°C or 15°C.
Relative humidity, condensation and mold:
a. The diesel generator set working conditions should comply with the following table.
Upper limit value of ambient temperature/°C
Maximum mean monthly relative humidity
Mean monthly minimum relative humidity
Created on Oct 8th 2018 04:44. Viewed 196 times.
No comment, be the first to comment.