Prostar low frequency 10kva upsby Orson Z. Overseas Trade Manager
|Place of Origin:||Guangdong, China|
|Brand Name:||Prostar or OEM/ODM|
|Certification:||CE, EMC,IEC,LVD,RoHS, ISO9001, ISO14001|
|Wave Form:||Pure Sine Wave|
|Transfer Time:||Zero Conversion|
|Battery Type:||SMF Lead Acid Battery|
|Product Features:||Industrial Low frequency online UPS|
|Built-in Isolated Transformer:||Yes|
|Protection:||Over voltage, Short circuit, Unbalanced loads, under Voltage, Battery under voltage|
|Application:||Data center,Instrumentation,Medical Equipment,Telecom,Secuirty/Alarm, Bank, Industrial, Telecom|
|Minimum Order Quantity:||10 Piece/Pieces|
|Price:||US $ 10 - 10,000 / Piece|
|Packaging Details:||Standard Export Wooden Package. The Safest Transportation Package|
|Delivery Time:||15~20 days for Routine machine, once received deposit|
|Payment Terms:||T/T or L/C. 30% deposit before production, 70% balance before shipment.|
|Supply Ability:||88000 Piece/Pieces per Month|
An uninterruptible power supply, also uninterruptible power source, UPS or battery/flywheel backup, is an electrical apparatus that provides emergency power to a load when the input power source, typically mains power, fails. A UPS differs from an auxiliary or emergency power system or standby generator in that it will provide near-instantaneous protection from input power interruptions, by supplying energy stored in batteries, supercapacitors, or flywheels. The on-battery runtime of most uninterruptible power sources is relatively short (only a few minutes) but sufficient to start a standby power source or properly shut down the protected equipment.
A UPS is typically used to protect hardware such as computers, data centers, telecommunication equipment or other electrical equipment where an unexpected power disruption could cause injuries, fatalities, serious business disruption or data loss.
[Keyword] 10kva ups, 10kva online ups, 3 phase 10kva ups, online ups 10kva, prostar ups, best ups
1)DSP digital control technology
Core system uses the world's most advanced all-digital DSP control technology, which can effectively guarantee the UPS' core system accurate, and fast running.
2)Advanced IGBT inverter technology
Combined high-reliable and high-efficiency IGBT inverter technology with high-frequency Pulse Width Modulation technology (PWM).
It could reduce noise and power loss, to ensure users can load in a variety of working situations and obtain high-quality voltage output and maximum cost-effectiveness, but also make input efficiency more than 95%.
3)Pure-online double conversion technology
Reliable and stable, after filtered and regulated, the output sine wave from pure-online double conversion technology, not only has the atmospheric disturbance suppression filter, but also with the standard output isolation transformers, static bypass, maintenance bypass, make this product with higher ability to engage in short circuit current. And it can be applied to the worst working environment.
Perfectly system protection functions: It has AC over-voltage, under-voltage, output over-voltage, under-voltage, output overload, short circuit protection, inverter, rectifier over-temperature protection, voltage under-voltage warning, battery over charging protection and other protections in one to ensure the system to operate stably and reliably.
5)Powerful Redundant Parallel Connection Function
Durable and reliable design of industrial-type modular structure, combined with full digital DSP control technology core system, make this product not only can be used for N +1 / N + X redundancy and the ability of enlarge the capacity, but also permit different power and different times of the UPS could be in parallel. It greatly reduced the user's pre-and post-purchasing costs, and increased capacity costs, but also expanded upper spaces of increasing capacity.
6)Powerful communication system
The standard equipped with RS232 interface, do contact relays, emergency switching device EPO input interface.
7)Low-power dissipation but high-efficiency
To achieve more than 98% of ultra-high efficiency under ECO economic model, which can effectively bring down the amount of electricity, and effective in accordance with the requirements of energy-saving target of the country.
8)Prediction warning system
LCD panel automatic detection function and timely warning in advance, with the boot self-diagnosis function. It could avoid the hidden danger in time due to UPS' failure, which caused risks. Also it could automatically alarm by setting the battery discharge to standby time is less than a set value.
9)Humanized panel display
Humanized panel settings, the users can set system parameters, date, output voltage, battery capacity, alarm function, light-load shutdown, system boot time, MODEM settings, such as orders, also it can be up to 120 abnormal failure information for users to query.
10)Super-strong environment adaptability
This product has superior environmental adaptability, wide AC input range, greatly reduces the frequency of battery using, and effectively extends the battery life.
11)Powerful Overload Ability
Using the pure-online double conversion technology, with the output isolation transformers, static bypass, and maintenance bypass.
Inverter Overload Ability reached 110% / 125% / 150% overloading time can last for 300min/10min/1min.
Bypass Overload Ability reached 150% / 170% / 250% overloading time can last for 60min/10min/1min.
- Industrial Automatic Control
- Medical Equipment
- Office Automation
- Production Equipment
- Electronic & Telecom
- Aeronautics & Astronautics
- Bank ATM
- Army Technology
- Securities System
One year warranty after the date of delivery.
Terms of payment is T/T or L/C. 30% deposit before production, 70% balance before shipment.
|1.Can I support Air-Conditioning on my UPS?|
|Air-Conditioning can be considered as a “dirty” load due to continual switching causing voltage and current spikes and surges. The UPS module can cater for a certain level of overload for a small duration, however the duration and level of current surges typically associated with A/C units is far greater than the UPS’ capability. Therefore it is advised not to support the AC on a UPS and supply this element with a generator only if possible. If there is no option but to support the AC using a UPS, it is normal to oversize the inverter by 4-5 times to ensure that the unit will cater for this more demanding load and eliminate any risk to the critical load. Another sensible approach to reduce any risk is toeth critical load is to have a seperate dedicated UPS for the A/C requirement.|
|2.Why choose 'Transformer-based' or 'Transformer-less' UPS?|
|Transformer based Traditional technology, typically available from 10 kVA, suitable for industrial applications, galvanic isolation with inverter output transformer, typically standard technology from 100 kVA upwards|
Transformer-less Typical technology from the smallest ratings up to 120 kVA, more compact footprints, lower weights, more suited to IT applications and environments, high efficiency across the load range, generally more cost effective.
|3.Can I add more UPS modules to the system when my load increases?|
|Yes, our SU, HM and HT ranges employ a plug and play parallel system that allows additional units to be added to an existing system at a later date. Additional UPS units can be added to either provide redundancy or extra capacity if the load increases. Sometimes it’s worth investing in additional switchgear early on so that more units can be accommodated much more easily.|
|4.Why do you need a UPS?|
|An Uninterruptible Power Supply (UPS) is used to protect critical loads from mains supply problems, including spikes, voltage dips, fluctuations and complete power failures using a dedicated battery. A UPS system can also be used to ‘bridge the gap’whilst a standby generator is started and synchronised.|
|5.Considerations when choosing a UPS and Generator combination?|
|It is usually beneficial to deal with one supplier for both items as this eliminates the potential conflict if the equipment does not work well together. Typical problems are related to input harmonics, load acceptance, poor frequency regulation, voltage intolerance and poor response times.|
|6.What is ECO mode?|
|ECO mode is often referred to as 'Active Standby' and is mainly used on sites where the general mains supply is relatively stable or the load is not senstive to mains interference. The UPS runs in bypass for normal conditions and transfers the load, without break, to inverter when the mains fails. This configuration is available on our entire UPS range upon request. This mode provides an improved system efficiency of around 98%.|
|7.Do I have to replace my UPS batteries with the same brand of batteries?|
|If you use brand X and need to replace one or two batteries in the string you should use the same brand because they will have the same characteristics. If you need to replace the whole string then you can change brands with fewer risks.|
|8.How can I ensure that my UPS batteries are maintained and serviced properly?|
|With proper maintenance, battery life can be predicted and replacements scheduled without interrupting your operations. These are IEEE and OEM recommendations for general maintenance:|
A.Comprehensive maintenance programs with a monthly inspection and more rigorous quarterly and annual checks
B.Re-torque all connections, as required
D.Cleaning the battery area, as required
|9.How is battery runtime affected if I reduce the load on the UPS?|
|The battery runtime will increase if the load is reduced. As a general rule, if you reduce the load by half, you triple the runtime.|
|10.If I add more batteries to a UPS can I add more load?|
|Adding more batteries to a UPS can increase the battery runtime to support the load. However, adding more batteries to the UPS does not increase the UPS capacity. Be sure your UPS is adequately sized for your load, and then add batteries to fit your runtime needs.|
Created on Dec 31st 1969 19:00. Viewed 0 times.